DIY OR CALL AN ELECTRICIAN WHOLE HOUSE SURGE PROTECTOR LINK
DIY PHONE LINE SURGE SUPPRESSOR LINK
DIY IN-WALL SURGE PROTECTORS LINK
QUICK GUIDE TO COMPUTER SURGE SUPPRESORS LINK
A surge protector (or surge suppressor) is an appliance designed to protect electrical devices from voltage spikes. A surge protector attempts to limit the voltage supplied to an electric device by either blocking or by shorting to ground any unwanted voltages above a safe threshold.
The terms surge protection device (SPD), or the obsolescent term transient voltage surge suppressor (TVSS), are used to describe electrical devices typically installed in power distribution panels, process control systems, communications systems, and other heavy-duty industrial systems, for the purpose of protecting against electrical surges and spikes, including those caused by lightning.
Many power strips have basic surge protection built in; these are typically clearly labeled as such. However, power strips that do not provide surge protection are sometimes erroneously referred to as “surge protectors.”
PRIMARY SOURCE OF SUPPRESSION:
A metal oxide varistor consists of a bulk semiconductor material (typically sintered granular zinc oxide) that can conduct large currents (effectively short-circuits) when presented with a voltage above its rated voltage. MOVs typically limit voltages to about 3 to 4 times the normal circuit voltage by diverting surge current elsewhere than the protected load. MOVs may be connected in parallel to increase current capability and life expectancy, providing they are matched sets (unmatched MOVs have a tolerance of approximately ±20% on voltage ratings, which is not sufficient).
MOVs have finite life expectancy and “degrade” when exposed to a few large transients, or many more smaller transients. As a MOV degrades, its triggering voltage falls lower and lower. If the MOV is being used to protect a low-power signal line, the ultimate failure mode typically is a partial or complete short circuit of the line, terminating normal circuit operation.
Transient Voltage Suppression Diode (TVS) diode is a type of Zener diode, also called an avalanche diode or silicon avalanche diode (SAD), which can limit voltage spikes. These components provide the fastest limiting action of protective components (theoretically in picoseconds), but have a relatively low energy absorbing capability. Voltages can be clamped to less than twice the normal operation voltage. If current impulses remain within the device ratings, life expectancy is exceptionally long. If component ratings are exceeded, the diode may fail as a permanent short circuit; in such cases, protection may remain but normal circuit operation is terminated in the case of low-power signal lines.
A Trisil is a type of thyristor surge protection device (TSPD), a specialized solid-state electronic device used in crowbar circuits to protect against overvoltage conditions.
A gas discharge tube (GDT) is a sealed glass-enclosed device containing a special gas mixture trapped between two electrodes, which conducts electric current after becoming ionized by a high voltage spike. GDTs can conduct more current for their size than other components. GDTs have a finite life expectancy, and can handle a few very large transients or a greater number of smaller transients. The typical failure mode occurs when the triggering voltage rises so high that the device becomes ineffective, although lightning surges can occasionally cause a dead short.
GDTs take a relatively long time to trigger, permitting a higher voltage spike to pass through before the GDT conducts significant current. It is not uncommon for a GDT to let through pulses of 500 V or more of 100 ns in duration.
GDTs create an effective short circuit when triggered, so that if any electrical energy (spike, signal, or power) is present, the GDT will short this. Once triggered, a GDT will continue conducting (called follow-on current) until all electric current sufficiently diminishes, and the gas discharge quenches. Unlike other shunt protector devices, a GDT once triggered will continue to conduct at a voltage less than the high voltage that initially ionized the gas; this behavior is called negative resistance.
Selenium voltage suppressor is an “overvoltage clamping” bulk semiconductor similar to a MOV, though it does not clamp as well. However, it usually has a longer life than a MOV. It is used mostly in high-energy DC circuits, like the exciter field of an alternator. It can dissipate power continuously, and it retains its clamping characteristics throughout the surge event, if properly sized.
Carbon Block Spark Gap Overvoltage Suppressor is one of the oldest protective electrical technologies still found in telephone circuits. A carbon rod electrode is held with an insulator a specific distance from a second electrode. The gap dimension determines the voltage at which a spark will jump between the two parts and short to ground. The typical spacing for telephone applications in North America is 0.076 mm (0.003″). Carbon block suppressors are similar to gas arrestors (GDTs) but with the two electrodes exposed to the air, so their behavior is affected by the surrounding atmosphere, especially the humidity. Since their operation produces an open spark, these devices should never be installed where an explosive atmosphere may develop.
Quarter-wave coaxial surge arrestor is used in RF signal transmission paths, this technology features a tuned quarter-wavelength short-circuit stub that allows it to pass a bandwidth of frequencies, but presents a short to any other signals, especially down towards DC. The passbands can be narrowband (about ±5% to ±10% bandwidth) or wideband (above ±25% to ±50% bandwidth). Quarter-wave coax surge arrestors have coaxial terminals, compatible with common coax cable connectors (especially N or 7-16 types). They provide the most rugged available protection for RF signals above 400 MHz; at these frequencies they can perform much better than the gas discharge cells typically used in the universal/broadband coax surge arrestors. Quarter-wave arrestors are useful for telecommunications applications, such as Wi-Fi at 2.4 or 5 GHz but less useful for TV/CATV frequencies. Since a quarter-wave arrestor shorts out the line for low frequencies, it is not compatible with systems which send DC power for a LNB up the coaxial downlink.
Series Mode (SM) surge suppressors devices are not rated in joules because they operate differently from the earlier suppressors, and they do not depend on materials that inherently wear out during repeated surges. SM suppressors are primarily used to control transient voltage spikes on electrical power feeds to protected devices. They are essentially heavy-duty low-pass filters connected so that they allow 50/60 Hz line voltages through to the load, while blocking and diverting higher frequencies. This type of suppressor differs from others by using banks of inductors, capacitors and resistors that shunt voltage spikes to the neutral wire, whereas other designs shunt to the ground wire.